Classe iso : 7
When air is compressed, the rise in its temperature increases its capacity to transport water in the form of steam.
It is then saturated with water vapour. As it cools, it loses this holding capacity and the water condenses.
It is essential to remove the liquid phases from the air before the other stages of its treatment: dryers are not designed to treat liquid water and the filter media can be damaged by it.
The WS separator is indispensable for all compressed air installations ! To be installed at the beginning of the line, before the tank, or after if there is a long length of pipe before the other stages of treatment.
This product is no longer in stock
* Select the generic if you don't know which model to choose. The sales department will contact you to determine the appropriate model.
(*) Flow rates indicated according to ISO 7183 (20ºC and 1 bar absolute) under 7 bar relative
Elimination of liquid phases at the beginning of air treatment.
Correction factor depending on operating pressure
|Percentage of liquid phases removed||100%|
|Maximum compressed air temperature||120°C|
|Minimum compressed air temperature||1°C|
|Maximum operating pressure||Depending on model|
|Pressure loss||<45 mbar|
|Standard drain||Automatic - float drain|